I tested the outlet and found no power was present. I removed the outlet and tested at the terminals, again no power (or so I thought). At this time I was wondering if this cable was connected. I removed the terminal screws to find that the cable was not prepared correctly, the terminal screws were lightly clamping the PVC insulation, the bare copper conductors were not in contact with the outlet. This picture shows the three conductors each with the terminal screw marks.
Luckily for the owner, the terminal screws were not in contact with the copper conductor, as this could have caused a fire.
Every day I work I see signs of sub-standard Electrical Work, clearly this installation was not undertaken by a qualified electrician nor was the installation tested. Yet another warning for consumers not attempt DIY electrical work.
If you have a power point not working, call me on 0431 232 796 to rectify the problems for you.
Looking for electrical supplies? Check out these bestsellers...